Low-Voltage Copper Core Armored Power Cable
Product model: ZR-YJV22
Product specifications: 3*240+2*120
1. The maximum rated temperature of the cable conductor is 90℃. When the short circuit(the longest duration not exceeding 5 s),the maximum temperature of the cable conductor does not exceed 250℃.
2.The ambient temperature when laying the cable should not fall below 0℃.
3.Bending radius allowed when laying: single-core cable is not less than 15 times the outer diameter of the cable; multi-core cable is not less than 10 times the outer diameter of the cable.
Conditions of Use
YJV copper core XLPE insulated power cables can be laid in the indoor,channel and pipe, can also be buried in loose soil, can not afford external forces.
YJV22 copper core XLPE steel tape armored sheathed power cable laid underground, can withstand mechanical external force, but can not afford a larger tensile force.
YJV32 copper cross-linked polyethylene insulated thin steel wire armored PVC sheathed power cable for high drop zone, the cable can withstand mechanical external forces and considerable tension.